Oxiperm Pro OCD-162-5/-10 Example Installation Scheme
For further information about the Oxiperm Pro OCD-162-5-10 Generator please call us on 01246 813110 or email email@example.com - Alternatively you can complete our online enquiry form.
Measuring and control unit
Dosing pump for sodium chlorite
Dosing pump for hydrochloric acid
Dosing pump for chlorine dioxide
Solenoid valve for dilution water
Dilution water line
Chemical tank (not in standard delivery)
Collecting tray (not in standard delivery)
Conditions for Installation
No outdoor installation, installation site must be protected against sun and frost, and well-ventilated
Protection against unauthorized access
The system has to be wall-mounted vertically, the component tanks have to be situated below the system
Temperature of dilution water 10 - 30 °C
Water connection 3 - 6 bars, floor-drain and appropriate mains supply must be provided.
Note: In case of quantity fluctuations in the main water flow, the use of a bypass mixing module (see Accessories) or the version with digital dosing pump is recommended, in order to optimise the blending and to minimise the risk of corrosion. We have more information on our Chlorine Dioxide page outlining additional information.
For further information about the Oxiperm Pro OCD-162-10 Generator please call us on 01246 813110 or email firstname.lastname@example.org - Alternatively you can complete our online enquiry form.